Membrane disc diffuser
Diffusers are developed specifically for releasing 1~3mm fine bubbles into water. Different materials were selected for their ability to withstand the effects of chemical and bio chemical agents, and 0~100℃ water temperature. The diffuser can be placed in an evenly distributed grid system at the bottom of an entire aeration tank. Air can then easily pass through the orifice and integrated non-return valve into water.The purpose of Bubble Diffuser is to dissolve oxygen into wastewater so that the microorganisms can utilize it while they break down organic material.
Air diffusers selection is critical to optimizing aeration in a lake, waste water treatment plant or pond. Let us assist you with matching the best available diffuser technology to the aeration application and to the air pressure provided by the compressor.
Operating air flow range(m³/h.piece)
|Designed air flow(m³/h.piece)||1.8||3.0||4.2|
|Effective surface area||0.3-0.65||0.4-0.8||0.5-1.0|
|standard oxygen transfer efficiency(%)||22-40||22-40||22-40|
|standard oxygen transfer rate(kg.O2/h.piece)||0.13-0.4||0.21-0.4||0.2-0.4|
|Acid alkali resistance||180-280||180-280||180-280|
Whole Aeration system included the aerator(bubble diffuser) gas distribution pipes, tees, crosses, elbows, regulators, connectors, cleaning devices and other components. Usually gas distribution pipelines is the usual circular arrangement, diffuser quantity is according to the air capacity and ponds size. The diffuser and gas distribution pipelines using G3 / 4 threaded connection, the base is inner thread (fixed in the pipeline), diffuser is externally threaded.
1.fix the regulator in the down of the ponds via expansion bolts
2.Install the gas pipeline into the regulator by using hoop,then adjust
3.To prevent the aeration equipment,should install the system after building works finished,then pour water into ponds.
4.To avoid leak between the pipeline and connection parts,should test the system by water in advance(water should be 10cm exceed the diffuser),then ventilate the system.
By considering the pressure balance, the best way of air pipe design is to connect all the pipes into a ring network. Inlet pipe valves for membrane disc diffuser should be set up each to conveniently adjust the volume of air. Air pipe designed velocity: main for 10-15 m/s; branch for 5 m/s. Installation height between surface of membrane disc diffuser and bottom of the ditch: 270 mm, 250 mm; the push plate type for 200 mm.